The self-starting generator is designed with an advanced control system and a dedicated program controller. When the mains loses power, lacks phase, or undervoltage, it can automatically start the unit and put it into operation. When a fault occurs, The audible and visual alarm device will automatically alarm, and can memorize the fault point, and can automatically unload and shut down to ensure the safety of the unit.Our portable electric generator is equipped with high-quality engines, and a variety of brands are available for customers to choose from.
（1）High thermal efficiency and low fuel consumption.
（2）Low operating cost, can use a variety of fuels, has low requirements on fuel quality, and is suitable for burning heavy oil with high viscosity, and the price of heavy oil is much lower than light diesel.
（3）High reliability, stable power generation. Normally, the power generation runs at 90% of the rated power.
（4）The load adaptability is strong, the fuel consumption rate changes little when the unit load changes from 50% to -100%, so the economy is good when the peak load is adjusted, and the range of adaptive load changes is large.
（5）The unit starts quickly and can reach full power very quickly. Generally, it only takes a few seconds to start a diesel engine. In an emergency, it can reach full load in 60 seconds, and under normal conditions (900 seconds-1800 seconds) Reach full load.
（6）The stand-alone capacity is small, and the operation and operation technology is relatively simple, which is convenient for general operators to master. Simple maintenance, convenient maintenance, fewer operators required, and low maintenance during standby.
（7）For generator sets that match high-pressure, medium-speed diesel engines, its structure is compact (high power per unit volume).
（8）Self-starting type, noise and vibration can be effectively controlled.
（9）Equipped with security support, easy location.
（10）Four-wheel trailer for more stability and traction.
We have several kinds of power and brands for you to choose. Please see what products we have. I believe there will always one for you.
Basic parameters of Yuchai mobile silent generator set：
Can be customized according to user requirements.
3.Start-up steps and precautions for diesel generators
（1）preparation before starting.
Every time before starting, you must check whether the cooling water or antifreeze in the diesel water tank is satisfied. If it is missing, fill it up. Pull out the oil gauge to check whether the lubricant is lacking. If it is missing, add it to the required"quiet full"scale, and then carefully check the relevant components for possible hidden troubles. If any failure is found, it should be removed in time to start.
（2）It is strictly forbidden to start the diesel engine with load.
Before starting the diesel engine, pay attention to the output air switch of the generator must be in the off state. After starting the diesel engine of the ordinary generator set, it needs to run for 3-5 minutes at idle speed (about 700 rpm). In winter, the temperature is low, and the idle speed should be extended for a few minutes. After starting the diesel engine, you must first observe whether the oil pressure is normal and whether there are any abnormalities such as oil leakage and water leakage. (Under normal circumstances, the oil pressure must be above 0.2MPa). If an abnormality is found, immediately stop the machine for maintenance. If there is no abnormal phenomenon to increase the speed of the diesel engine to the rated speed of 1500 rpm, at this time the generator displays a frequency of 50HZ and a voltage of 400V, then the output air switch can be closed and put into use. The generator set is not allowed to run without load for a long time. (Because long-term no-load operation will cause the diesel injected by the diesel injector to not completely burn and cause carbon deposits, resulting in valve and piston ring air leakage.) If it is an automated generator set, you do not need to run at idle speed, because automated units generally Equipped with a water heater, the diesel engine cylinder is always maintained at about 45 ° C. After the diesel engine is started, it can normally transmit power within 8-15 seconds.
（3）pay attention to observe the working status in operation.
In the work of the generator set, there must be a special person on duty, often pay attention to observe a series of failures that may occur, especially pay attention to changes in oil pressure, water temperature, oil temperature, voltage, frequency and other important factors. In addition, it is necessary to pay attention to having enough diesel oil. If the fuel is interrupted during operation, it will objectively cause a shutdown with load, which may cause damage to the generator excitation control system and related components.
（4）it is strictly prohibited to stop with load.
Before each stop, the load must be cut off gradually, then the output air switch of the generator set should be turned off, and finally the diesel engine should be decelerated to idle and run for about 3-5 minutes before stopping.